TNS single, three-phase high-precision fully automatic AC voltage regulator
系列单、三相高精度全自动交流稳压器（稳压电源），由接触式自耦高压器、伺服式电动机、自动控制电路等组成，当电网电压不稳定或负载变化时，自动采样稳压器控制电路发出信号驱动伺服电机，调整稳压器自耦调压器碳刷的位置，使稳压器输出电压调整到额定值并达到稳定状态。 SVC series single-phase and three-phase high-precision full-automatic AC voltage stabilizer (regulated power supply), consisting of contact auto-coupler, servo motor, automatic control circuit, etc. When the grid voltage is unstable or the load changes, it will automatically sample The voltage regulator control circuit sends a signal to drive the servo motor to adjust the position of the carbon brush of the voltage regulator autocoupling regulator, so that the voltage regulator output voltage is adjusted to the rated value and reaches a stable state.
This series of voltage regulators are ordinary type and have the function of mains pass-through. This series of voltage regulator products have many varieties, full specifications, beautiful appearance and other advantages. It has the characteristics of undistorted waveform, high efficiency, reliable performance, and long-term operation. The voltage stabilizer has protection functions such as short delay and overvoltage. Long delay and undervoltage protection can be added according to user needs. This voltage stabilizer can be widely used in any place where electricity is used. It is an ideal regulated power supply (voltage regulator) to ensure the normal operation of your electrical equipment.
This voltage stabilizer can be used in office equipment, test equipment, medical equipment, industrial automation equipment, household appliances, lighting systems, communication systems and any other place where electricity is used.
、本系列稳压器只能室内使用，请按照正常使用条件使用。 1. This series of voltage regulator can only be used indoors, please use it in accordance with normal conditions of use.
、本系列三相稳压器输入为三相四线制接线，在缺零的情况下不能正常使用，否则会导致稳压器损坏。 2. The input of this series of three-phase voltage regulator is three-phase four-wire system wiring, which cannot be used normally in the absence of zero, otherwise it will cause damage to the voltage regulator.
、为保证稳压器正常输出电压、电流，减少线路功率损耗，请合理选择输入、输出导线截面积，一般选用铜芯导线 接5A/mm2计算，若选用铝芯导线则按2.5A/mm2计算。 3. In order to ensure the normal output voltage and current of the voltage regulator and reduce the line power loss, please choose the cross-sectional area of the input and output wires reasonably. Generally, copper conductors are connected to 5A / mm2 for calculation. Calculation.